for KNIGHTDALE, NC
Brian - Knightdale, NC
Dwayne immediately diagnosed the problem as a faulty gas valve. Replaced promptly the same afternoon. He reviewed our records and saw that we had the same problem before and waived the service charge. Nice to see a service tech and company that make things right when it’s no fault of there’s.
Terry - Knightdale, NC
Earl did a great job with a difficult project. The parts were not easy to find but he stuck to it and found what was needed. My shower is now working. Thank you, Earl.
Replaced back water valve
Main sewer pipe clog with back water valve
Main line clog
Gas Valve on 50 gallon water heater
Washer shut off
Ihop Knightdale (main sewer stopped up)
Leaking toilet. Supply line replaced and fill valve.